The MSTAT is a fuss free, simple to use manually operated thermostat.
MOUNTING OF FLOOR SENSOR:
MOUNTING OF THE THERMOSTAT:
The single gang mounting box must have a depth of no less than 35 mm.
1. Use a screwdriver in both sides to open the lock. The cover must be dismounted.
2. Connect cables.
3. The thermostat is mounted in the wall socket. The cover is remounted.
Please note: As with all electrical projects which are subject to Part P Building Regulations, all elecrical work should be carried out by a certified/qualified electrician. All work must conform to BS 7671:2008 and the current IEE Wiring Regulations.
|Manufacturer Part Number||MSTAT|